Cbus to KNX Bus Translator software 1.1.0 fixes the following bug;
Custom Applications could not be selected if they have the same Group address a the lighting application (56) in Cbus to KNX Mapping Table
For example if Lighting Applixation group address 1 is in the Cbus to KNX Maping table, the Custom application 136 (and any other custom applications) could not select Group address 1
In KNX to Cbus Tab, Cbus addresses in the same application can be duplicated on different rows provided the KNX object in the rows have different types, eg KNX 0/0/1 1-bit and 0/3/1 scaling can be mapped to the same Cbus lighting address.
In Cbus to KNX Tab, Cbus Group Addresses in the same Application can be duplicated if they are mapped to different KNX Address Types. eg if the 1st entry in Cbus to KNX is Lighting Group Address 1 mapped to KNX telegram type on/off, you can add another mapping of Lighting group Address 1 to KNX Type Scaling (but not to another KNX On/Off Telegram type).
BUG caused by No 2 above. In C-Bus to KNX, if a CBus in eg Lighting Group address is mapped to a KNX Telegram Type, the same C-Bus Group address in another application cannot be mapped to the same KNX Telegram Type
Please revert to 1.1.0 if you use the same cbus group addresses in different applications
Last edited on Saturday Jul 20th, 2019 07:12 am by slychiu