I have recently purchased a farfisa PL11P bundle with a DM02, I have successfully installed the door station and DM02 and all is well.
Now I need Comfort to open my gates via the keypad and this is where my knowledge and programing of comfort is limited.
Any help will be much appreciated
Here are the instructions to open door/gate using DM02 Programming the Door/Gate Relays
A door strike or automatic gate can be opened from the Door Station menu. The two menu commands; “4 to Open Gate, 7 to Open Door”
can be programmed to open a gate or a door using a relay connected to any Comfort output or the relays K1 (Gate) and K2 (Door) on the DM02.
Go to Comfigurator > Events > Miscellaneous Events and look for the events Open Door Response and Open Gate Response in the list.
Select or create a Response to be assigned to Open Door Response and Open Gate Response as required. If no Response is selected, the corresponding menu to Open Gate and/or Open Door will not be announced. Once a nonzero Response is selected, the corresponding menu item will be announced.
To control the relays K1 and K2 on a DM02, use Action 200 (Open Door). In Response Wizard select Output > Open Door, then select the Door Station ID, the Door number 1 for K1 (Gate) and 2 for K2 (Door), and the duration in 100 ms units.
If there is more than 1 Door Station, use the IF Door Station ID action to program the outputs according to the ID of the door station eg
If DoorStationId = 49 Then
Pulse Output01 For 20
If DoorStationId = 50 Then
Pulse Output02 For 20
If DoorStationId = 51 Then
Pulse Output03 For 20
The above Response for Open Gate or Open Door Response will pulse Output 1 for DP ID 1, output 2 for DP ID2 and Output 3 for DP ID 3.