Comfigurator 3.13.6 (Beta) is available from http://www.cytech.biz/comfigurator.html
Please note that there was a previous beta with the same 3.13.6. If anyone has installed this please uninstall before installing this again. The date om the Comfiguraor 3.13.6 should be 10 Novemnet 2020
• wifi01 SSID and Passcode settings do not allow spaces Bugs Fixed
Action set Virtual Input does not select Virtual Input, selects physical input instead
And/OR actions are wrong for read from comfort. Now actions involving And/Or conditions after Read from Comfort will appear as Branch instructions, instead of If/Else instructions.
Set login partition Action error was fixed
Security Mode Responses and siren outputs programmed in old cclx files were not in Partition events.
Cbus to Comfort Output status is wrong when mapped to lighting group address. Output -1 status was shown instead of output number status
IRIO Analog Output Proportional + Integral Mode Changes for each Analog Output: Added Direction mode for PI control, Change text Integral time (secs) to Integral Time (samples), Add parameter Sample time (secs). Gain (K) range changed from (0 to 15.93) to (0 to 31.875)
IRIO Added Submodule Type 9 PT1000 (This hardware is not yet available)
IRIO Added Input Type 8 applicable to PT1000 Teperature sensor. (This hardware is not yet available)
Last edited on Saturday Nov 14th, 2020 03:19 am by slychiu
I confirm as well, that 3.13.6 correctly remaps the armed events.
I agee with Gary that a link in the upgrade advise window, pointing to an html page containing ALL the previous changes (and not only the latest) whould be useful. The page should contains the change history for each version, because not everyone is aware of/has installed all the step-middle versions.
I was having issues with my partitions on my system esp arming/disarming responses made sure all firmware was up to date problems persisted and just down graded comfigurator too Comfigurator3.13.5 everything seems to be wroking correctly again!
I am unable to set input 17 as a virtual input.
When creating a responce i select zone17 from the dropdown but it will not stey selected it always goes back to zone1.
Also zone1 is now configured as a virtual input and i cannot remove it.
Virtual Inputs cannot be created by a Response. They have to ve selected as Vietual Inuts through an external device like KNX, Modbus, Cbus etc
Sened the cclx file to email@example.com will reset the Virtual Input for zone 1 and add zone 17 as virtual