UCM/Cbus2 v7.045 is the released version of UCM/Cbus2
Please note of the bug in the firmware which was recently discovered
Enable and Trigger application map to counter does not work
When UCM/Cbus2 is reset, the Status report from the lighting application does not update counters. Only a hard reset ie removing power from ucm/cbus2 will update Comfort counters based on thye Lighting application. The effect of this is minimal, as it can be seen only after Comfort firmware is upgraded when the lighting groups addresses values in the mapped counters will not be correct unless the status of the lighting groups first changes
Last edited on Wednesday Jul 30th, 2014 09:19 am by ident
Added new setting in UCM/CBUS2 to enable or disable the periodical resending of Options to the CBUS SIM module. In previous firmware, UCM/Cbus2 resends the 3 SIM Options every 60 seconds to the SIM to solve a problem found by only a few users that after weeks or months the UCM/Cbus went into a different mode where it did not receive messages from Cbus. This is believed to be caused by the Cbus side. The periodical resending of SIM options is meant to ensure that the SIM always stays in the correct mode. The new setting requires a change in Comfigurator (after 3.88). By default after upgrading the firmware, the resending of SIM options is disabled.
In addition to the above, when the resending of SIM options is enabled, the update of security zones to the Cbus Security application (zone sealed and unsealed) will not be repeated as it is not necessary and causes extra traffic on Cbus
Last edited on Saturday Jul 5th, 2014 07:28 am by ident