Engineer Menu 4,5 Keypad Area (Anouncement) is wrong.
Execute Response in Comfigurator (DA) with multiple actions - security alarm actions eg bypass, Do Alarm cause subsequent actions do not work. eg Bypass zone 1, bypass zone 2, output 1 on Only Bypass zone 1 will work. However the Response executed by Comfort events will work
Bypass action has other problem of clearing a memory bit
Partition keypad disarm does not off siren when disarm partition if there is a trouble alarm, until the code is entered 2 times
CM9000- OPT firmware bug Clear all outputs action 8 does not work
Do Action 190 serial command DABE does not do the actions following action 190 correctly. The 1st action is continually repeated
Action 73, 16 Get keypadId/ If Keypad ID does not work
Fixed bug Security Check sometimes announced zones from several Partitions instead of the keypad's own partition
New Features and Improvements
Infrared Transmission improved performance for narrow IR signals mark/space. This requires UCM IR learner with improved IR receiver
When there is a Sensor value change from external UCM ids, the sensor Report from Comfort will be ignored by the UCM which originated it, so as to avoid dpuble updating which may cause a race condition
For Time Programs if a day is Holiday, then Days of week Monday to Sunday will be disabled. Hence a day in Time program is Monday to Sunday only if the day is NOT also a Holiday. The old way of operation was if the day is Holday, the Time program is also activated based on Monday to Sunday
Comfort automatically detects LEM03 connected, and overrides Comfigurator > Configuration> Modules and Settings checkbox for "LEM03 Connected"
Last edited on Saturday Dec 9th, 2017 02:49 am by slychiu