I have posted here as requested.
""Hi Ident, I have updated to the latest comfigurator, cbus firmware and Ultra Firmware, now for some reason some flags show as off in Comfigurator but on in the Android app and my responses that used to turn the cbus lights off have stopped working. Do you know what can be causing this?"
I don't think the issue is with Cbus as I can send a direct response to CBUS from comfort and it works fine. For some reason however flags that should be set to on to turn off lighting after a set time (and other flags that are not for CBUS) appear to be on in the android app but off in comfigurator.
Last edited on Sunday Apr 20th, 2014 07:26 am by waynebr
UCM/CBUS2 response wizard has a different format from ucm/cbus1 so after upgrading from cbus1 to ucm/cbus2 you must write to Comfort so the responses are updated
This is why execute response works in Comfigurator but not in Comfort when Responses are executed, as Comfigurator sends the actions direct to Comfort
In the UCM/Cbus2 post there is a warning IMPORTANT
The C-Bus actions in the cclx file are automatically converted to a new format for UCM/CBUS2, as the formats of the commands in Comfort are not compatible. WRITE to COMFORT now so that the new action formats are updated to Comfort. Save the upgraded cclx file under a new name so that the old cclx file can be retrieved if you wish to downgrade back to UCM/CBUS1
HI Ident, I tried the full re-write and this didn't change anything - I then tried editing one response and then uploading. This looks like it may have fixed the issue with the flags. Looking through my CBUS responses and checking the counters I may have identified the issue. For some reason the responses to turn the light on send looks correct but the one to turn off checks it for a different counter value, I'm not sure but I think previously it may have worked as a percentage but now it is on a true value.